The AmbiPlate 20 system is designed to suit battened floor buildups but can be easily adapted to suit sprung sports floors, acoustic batten floors and over-battened floors. Before the underfloor heating system is installed, insulation should be laid between the battens and should be laid as close as possible to the underside of the pipework to maximise heating output. The system consists of aluminum diffuser plates being fixed directly on to the battens. The plates contain grooved channels into which the underfloor heating pipework is installed in continuous lengths and piped back to the underfloor heating manifold. The reflective properties of the aluminium diffuser plates mean that any heat is efficiently pushed up through the sub-floor layers for maximum heat output. The nature of the system means that it has a quicker response that a traditional (screed) UFH system.
|Product||Code||Quantities Required||Component Images|
|17mm UFH Pipe||41010||6 linnear metres per m2 of heated area|
|Manifold||41320||Depends on heated area - normally approx 1 port per 20m2 of heated area.|
|Manifold Couplings||42200||For 17mm Ambiente pipe|
|Isolating Ball Valves||42050||1 pair (sold in pairs) per manifold|
|Manifold Tag||46755||1 per manifold|
|Pipe bends||41050||2 per port (used to form a neat bend in the pipe beneath the manifold)|
|Pumpset/blender unit||41434||1 per manifold|
|Aluminium diffuser Plate||44520||Allow 2.2 plates per m2 of heated area|
|Clout Nails (25mm)||41501||Allow one bag per 50m2 total area|
Please note that the above quantities are only guides, and not intended to cover every situation. Factors such as the heat source, heat loss and other parameters will affect the quantities of some products required.
See the AmbiPlate 20 system in action
Not sure which system would best suit your requirements? No problem, just fill in the basic details below, and one of our team will be in touch to discuss and reccomend the best solution.